Leave us a message...
If you are reading this EVOHOME Help! post, the likelihood is you now own a Honeywell evohome product… Congratulations, you have made an excellent choice and have one very clever money saving device in your home!
My personal experience of the Honeywell evohome system is that it is very easy to install and configure. However, since our launch in 2014 we have experienced emails and calls from customers with evohome ‘problems’. Sadly the same issues are occurring - incorrect installation/testing and/or the binding/system configuration is not being done correctly.
Below is a list of problems we are often called or emailed about.
1. Heating Zone Valve BDR91 Wireless Relay Box turning on at the same time as the Hot Water Zone Valve BDR91 Wireless Relay Box.
2. BDR91 Wireless Relay Box ‘COMMS FAULTS’.
3. HR91/92 Radiator Controllers not responding to evohome Controller.
4. CS92 Hot Water Sensor showing hour glass symbol.
5. evohome Controller not responding how it is ‘expected’ it should.
6. HCC80R Underfloor Heating Controller not responding to evohome Controller.
The main reasons these errors occur is because the evohome Installation Guide is not being followed or the evohome system is not understood correctly.
A copy of the evohome Installation Guide is in the bottom evohome Connected Thermostat Pack box and it is also available to download here >>> EVOHOME INSTALLATION MANUAL
The evohome Installation Guide was not written to be an A-Z manual on how to fit evohome, it is a technical booklet aim at reminding an installer how to do certain tasks with the evohome system. I will reference the evohome Installation Guide page numbers throughout my help page below and as they say in the trade – RTFM!
So, to try and prevent installation errors being the route cause of your evohome issues, I will list some of the common ‘problem’ areas and how you can avoid these basic errors causing problems with your evohome system.
Honeywell Feature Article – Wireless When & Where?
This is a very good document and reading this article will give you a better understanding of Honeywell wireless heating products and why correct installation is critical to the success of wireless controls working correctly. You can download this article by clicking here >>> WIRELESS WHEN AND WHERE?
Have a good read of this document first, just to give you an idea of what you are aiming to achieve and then if you are still having issues with specific evohome products use my help tips listed below.
An alternative approach maybe to do the evohome online training. This will give you a good feel for what the evohome system needs and will certainly answer a lot of installation questions we have. The evohome online training is here >>> EVOHOME ONLINE TRAINING
I have categorised the common issues we have into menus. If you are having issues with individual items this will allow you to scroll to the relevant item.
1. BDR91 Wireless Relay Box
2. T87RF Wireless Room Thermostat
3. HR91 Wireless Radiator Controller
This is a Radio Frequency (RF) device and must be positioned with care so that the wireless signal can easily be sent and received to and from the evohome Controller.
We are finding the same problem keeps cropping up with these – incorrect installation and ‘double binding’.
The BDR91 Wireless Relay Box that comes with the evohome Controller in a Connected Thermostat Pack will come pre-bound as a ‘Boiler Relay’ and this is causing some issues, especially when using the evohome Controller in conjunction with the evohome Hot Water Kit on S-Plan, S-Plan Plus or Y-Plan systems (heating systems containing motorised zone valves).
So lets start with the basics!
As per Page 4 of the evohome Installation Guide, BDR91’s must be installed a minimum of 300mm away from the following (no exceptions unless you want future evohome system problems!):
If the above points are not observed the evohome Controller RF Signal Tests to the relevant BDR91’s may still give an ‘excellent’ or ‘good’ wireless signal strength test, but it does not mean the wireless items will work correctly when put into normal operation mode.
It is also very important you try and visualise a path for the RF signal between the evohome Controller and the BDR91(s). If there is anything large and metallic in the ‘line of RF’ the likelihood is that the signal strength will be weak or simply won’t work.
Also in my experience it is really good practice if you just go ahead and make sure the BDR91’s are fully factory reset (‘BDR91 Reset Procedure’ is on Page 19, Step 1) as soon as the BDR91 has been wired up, before you even think about binding the system.
Honeywell wiring diagrams for the correct wiring of BDR91’s for Combi Boilers, Motorised Zone Valves and S Plan and Y Plan systems is on Page 44 to Page 47 of the evohome Installation Manual and the ‘BDR91 reset procedure’ is on Page 19, Step 1 (it says press and hold the button for 15 seconds, but in practice just press and hold until you get a fast flash which occurs at a count of about 15 seconds – ignore the ‘slow’ flash after 5 seconds at this stage).
An important note on the term ‘Boiler Relay’!
‘Boiler Relay’ seems to cause some confusion amongst a lot of people when binding the ‘heating BDR91′. A ‘Boiler Relay’ is the term Honeywell give when using a BDR91 to create a ‘wireless boiler demand switch’ i.e. a relay dedicated to switching the boiler on and off. If you have an S Plan or Y Plan system and the motorised zone valves are switching on the boiler using the orange wires, then you don't have a 'Boiler Relay'.
So, basically if you have the following situations, you should bind the heating BDR91 as a ‘Boiler Relay':
If you are using the evohome Connected Thermostat Pack & evohome Hot Water Kit on an S Plan or Y Plan system, you will not need a ‘Boiler Relay’ and this function must be ignored when you are asked the question when going through ‘ZONE GUIDED CONFIGURATION’ on the ‘INSTALLATION MENU’ of the evohome Controller!
The T87RF is the wireless thermostat part of the Y87RF2024 Single Zone Thermostat and can be used with evohome as a wireless sensor or bound with a BDR91 through evohome to provide zone control of a motorised valve, etc.
The main question we have with the T87RF is that the supplied ‘User Guide’ does not detail how to clear the pre-bound BDR91 ‘binding’ or how to ‘bind’ the T87RF with evohome.
Unlike any other Honeywell thermostat, the T87RF has two hidden ‘touch areas’. The left hand touch area is for binding the device to a ‘control system’ (such as a BDR91, HCC80R or the evohome Controller) and the right hand touch area is for binding the T87RF to the RFG100 Mobile Access Kit (should you wish to use it as a stand alone Connected Programmable Thermostat).
You can tell when you correctly put your finger in the ‘touch area’ as the screen will illuminate. Please note that when the T87RF is used with evohome, the right hand touch area has no function.
So, to bind the T87RF with evohome as a sensor please refer to the supplied Y87RF2024 User Guide for details on the locations of the touch areas but follow my procedure detailed below.
A few important points to note about binding the T87RF as a ‘sensor’ when controlling a room with HR92’s. If you bind any external sensor and adjust parameter 7 on the HR92 to 7.1 to show the actual temperature in the room, the HR92 will display the temperature of the T87RF instead of the temperature sensed by the HR92 - this does cause confusion and phone calls from customers stating the HR92's temperature display has 'jumped' to 30 degrees as they are holding the T87RF in their hand!
The HR91 Radiator Controller is a wireless digital radiator controller. Unlike the HR92, the HR91 has a simple LED user display which displays its function and faults. Unfortunately the guide provided with the product isn't great, but there is a better overview document of the HR91 Radiator Controller which can be downloaded here (HR91 Radiator FAQ's). The HR91 Radiator Controller has two buttons. The one on the left is the 'override' button, and the one on the right is the 'status' button. It also has a locking bezel at the bottom of the radiator controller. We have produced a HR91 help video which we will provide a link to shortly.
That is all for now. I will keep updating this section as an when I have things I think are important, but any technical questions in the meantime please give me a call, email or use our forum - http://theevohomeshopforum.co.uk/!
Thanks very much for reading so far!
Richard Burrows – Technical Director – The EVOHOME Shop